The Dimplex EUHB Series Industrial Grade Electric Unit Heater is designed with a rugged cabinet that is constructed of 18 gauge die formed steel. The units have individual adjustable 20 gauge convex profile air directing louvers. The louvers are friction fastened to a single piece 20 gauge frame to prevent movement once adjusted to the desired position.
Hybrid polyester epoxy powder coat paint finish
Finned tubular heating element
Motor: heavy duty, continuous operation, totally enclosed, thermally protected with permanently lubricated ball bearings
A jumper is provided to disable built-in thermostats when remote thermostats
CSA certified and UL approved
Unit heaters should be located along outside walls to provide perimeter air circulation. The discharge air should wipe the walls without blowing directly on them.
Small rooms can be heated by one or two units. Locate the unit heater(s) to provide circular air movement within the space.
Large rooms will require multiple unit installations. Units should be located so that the discharge air from one unit supports the discharge from another unit and provides a circular air movement.
Dimplex EUH10B74CT Industrial Grade Electric Unit Heater Installation Instructions
Dimplex EUH10B74CT Industrial Grade Electric Unit Heater Sales Bulletin