Results You searched for: K Series 208 Volt Baseboard Heaters Results Displayed: 1 - 10 of 10
King Electric K Series 208 Volt Baseboard Heaters
The K Series baseboard heaters are an economical way to provide heat. They are typically used in apartment construction and other rental properties because of the low initial cost and low maintenance. Quality components guarantee a long lasting reliable heater. Standard color is almond. Special Colors available: Customer must provide sample or color chip at time of order however due to our painting system color matching may not be exact. Four weeks or more lead time is required on all special color baseboard orders. Special pricing will apply. Institutional grade with 18 gauge front covers and 22 gauge back cans are available for special applications. All other specifications are the same as the standard heater.
NOTE: Baseboard Heaters are to be mounted on outside walls to wash the coldest part of a room with a blanket of heat.
Back Wire Design
Built-in Cable Clamps
All Aluminum Element Design
Full Length Safety Cutout
Baked Enamel Finish
Standard Color - Almond. Also available in Bright White Color
20 Gauge Front Cover
22 Gauge Back Can
Soft Contoured Corners
All Knockouts are 7/8 Inch Diameter for 1/2 Inch Conduit
Optional 18 Gauge Front Cover
Single or Double Pole Thermostat
The heaters shall take room air in the bottom (lower front) and discharge it through the top front.
The heaters back, bottom, and top shall be fabricated from electro galvanized 22 gauge steel. Front panels shall be fabricated from 20 gauge electro galvanized steel, ribbed longitudinally for extra strength and have center support to resist impact loads.
The heater casing shall have modern rounded ends and corners to provide a smooth appearance and finished with a baked enamel.
The heater shall be provided with a continuous capillary sensor tube, for thermal protection, extending the full length of the heating element, rated at 175º F, and be fail-safe type.
The heater shall have a 44 cubic inch junction box at both ends, furnished with five 1/2 inch knockouts located on the back, bottom, and side.
Heater elements shall consist of high quality 80% nickel and 20% chromium alloy resistant wire completely surrounded by magnesium oxide and enclosed and swaged in a rust resistant sheath. Ribbon aluminum fining shall be compression welded to the sheathed element to provide chimney type flue for heat transfer.
Heaters shall be supplied with a one year limited warranty.
Ratings and Approval
Available in ratings from 375 through 1,500 Watts at 120 Volts, and 375 to 2,500 Watts at 208-240 and 277 Volts.