Results You searched for: King Electric WHFC Series 240 Volt Ceiling Heaters Results Displayed: 1 - 6 of 6
King Electric WHFC Series 240 Volt Ceiling Heaters
Grill Dimensions: 13-1/2" L x 1/2" W x 10" H
Rough-In Cut: 12" L x 4" W x 9" H
Dual Open Coil Element
Squirrel Cage Blower
New Dual Limit
20 Gauge Powder Coated Grill with contemporary die formed round corners.
Standard Color - Bright White (Optional Color - Almond)
20 Gauge Electro-Galvanized Steel Recess Can with QuickSet™ stop on the side.
Factory installed ground wire. Approved for direct contact with building insulation.
Ratings: Heaters shall be available in wattages of 500 to 1,500 at 120, 208, or 240 volts.
Blower and Motor: A tangential cylindrical blower, delivering 65 CFM, shall be driven by a shaded pole, permanently lubricated, C-frame type motor with impedance protection and sealed bearings. Motors shall be the same voltage as the heater. The motor and all wiring shall be totally isolated from the heating chamber for protection from heated air.
Elements: Elements assemblies shall be constructed of coiled nickel chromium alloy, corrosion resistant wire strung through a minimum of four rows of mica insulator. Element assemblies shall have factory provided connection to allow field modification to 50% wattage
Thermal Overload: Heaters shall be equipped with thermal overload SMART LIMIT PROTECTION™, which disconnects elements and motor in the event normal operating temperatures are exceeded. If thermal overload trips due to abnormal operating temperatures, thermal overload shall remain open until manually reset by turning the heater off for fifteen minutes. Automatic reset thermal overloads, which allow the element to continue to cycle under abnormal conditions will not be accepted.
Wall Can: The wall can shall be 22 gauge electro-galvanized steel and shall contain knockouts through which power leads are brought. The wall can shall be provided with a depth gauge, extending the full length of the wall can. The wall can shall be supplied with a factory installed grounding wire.
Grill: The grill shall be louvered, one piece design with rounded edges on all four sides, with rounded corners to prevent snags from contact with other materials. The grill shall be epoxy powder coated in the color specified by manufacturer.
Approval: Heaters shall be listed and approved by Underwriters Laboratories