Results You searched for: Stainless Steel DAW Series 240 Volt Wall Heaters Results Displayed: 1 - 1 of 1
King Electric Stainless Steel DAW Series 240 Volt Wall Heaters
A heavy duty industrial switch mounted on the grill allows easy choice of 7 different power settings with ease. Use where higher wattage is not required during unoccupied periods and freeze protection may be achieved with energy savings. Quiet operating tangential blower and commercial grade element make the Dial-A-Watt the heater of choice for people on the move. Typical installations are boats and pleasure crafts where corrosion resistant construction is required. By providing air movement and dry heat, must and mold odors are reduced.
During use, the heater load (Amperage) can be adjusted to the shore power cord that is feeding the vessel. This prevents damage to plugs and receptacles due to over loading. During unoccupied periods, wattage can be adjusted to the correct level for freeze protection.
304 Stainless Steel Pic-A-Watt® Element
Squirrel Cage Blower
Flange Mount Wall Can
Multiple Wattage Selection
20 Gauge Clear Powder Coated Grill with die formed square corners
Green Pilot Light indicates when heat is on
Bimetallic limit turns the element off when an over temperature condition occurs and automatically
resets when the normal temperature returns.
Manual Reset Limit turns heater off and is reset by thermostat. 1-Pole or 2-Pole unit mount thermostat 45°- 80°F
Optional Surface Wall Box
Ratings: Heaters shall be available in wattages of 250 to 2,250 at 120, 208, or 240 volts.
Blower and Motor: A tangential cylindrical blower, delivering 70 CFM, shall be driven by a shaded pole, permanently lubricated, C-frame type motor with impedance protection and sealed bearings. Motors shall be the same voltage as the heater.
Elements: Elements assemblies shall be non-glowing design. Element assemblies shall consisting of steel sheathed heating tubes in a furnace brazed, plate finned, block design. Each sheathed tube shall contain coiled a Ni-Chrome wire, embedded in an insulator of magnesium oxide.
Thermal Overload: Heaters shall be equipped with thermal overload protection, which disconnects elements in the event normal operating temperatures are exceeded. The thermal overload protection
device shall automatically reset when normal operating temperatures are reached or manually reset by the thermostat.
Wall Can: The wall can shall be stainless steel and shall contain a minimum of three (3) knockouts through which power leads are brought. The wall can shall have a depth gauge or flange mount, and a factory installed copper grounding wire. Minimum Clearance to Floors and Sidewalls. Zero clearance to combustibles.