Results You searched for: TPI Corp/Markel 5600 Series Multiple Wattage Fan Forced Unit Heater Results Displayed: 1 - 4 of 4
CASING: Fabricated of die formed, heavy Gauge steel and finishedwith two tone, brown and beige, durable powder coated paint. Supply air is drawn through the rear heavy duty expanded steel inlet grill. Heated air is discharged through front adjustable louvers, which are spring loaded for individual adjustment.
ELEMENT: Heavy-duty block finelement design. The multiple tap electric connection design allows fieldconversion to eight wattage settings at 208/240-Volt single phase or 240/480 Volt, 3 phase. Units are available on special order with a specific wattage/voltage setting.
MOTOR: Motor shall be totally enclosed, permanently lubricated, all angle industrial rated with thermal overload protection.
WIRING: Wiring to terminal block adjacent to incoming knockout in accordance with NEC and local codes.
THERMAL OVERLOAD: All heaters shall be equipped with an automatic reset thermal cutout to shut down the element and motor circuits if unsafe operating temperatures are exceeded.
CONTROLS: The heater shall have a heavy-duty hydraulic thermostat factory installed and wired. All controls and wiring shall be in a large wiring compartment with hinged door for easy access. An optional disconnect switch shall be available for field installation.
MOUNTING: Heaters are standard with a three position-mounting bracket for wall, ceiling or workbench. Heaters can be mounted for horizontal or vertical discharge. Note: Minimum mounting height is 6 feet, and minimum distance from side of heater to nearest wall is 6 inches. Note: Approved for residential applications.