Results You searched for: W Series 240 Volt Wall Heaters Results Displayed: 1 - 50 of 59
The W heater is designed to be the highest quality economy heater available. It is commonly used in apartment construction and as a supplemental heater in single family homes. This heater mounts vertically and produces 85 CFM with a 4-bladed fan. The grill has die formed corners for a modern appearance, and is painted with a powder coated finish for extreme durability. Standard color is bright white, optional colors are available. Use it with a wall thermostat or a built-in one that can be field or factory installed. For surface mounting, a powder coated wall can may be purchased separately.
* Smart Limit Protection® * Dual Open Coil Element * C-Frame Motor * Aluminum Fan, 4-Blades * New Dual Limit Controls * Inlet and Outlet Sensing * Dual Wattage * 20 Gauge Powder Coated Grill with contemporary die formed round corners. * Standard Color - Bright White * 20 Gauge Electro-Galvanized Steel Recess Can with QuickSet™ stop on the side. * Factory installed ground wire. * Approved for direct contact with building insulation. * Optional Surface Wall Box * Optional 1-Pole or 2-Pole unit mount thermostat 45°- 80°F operating range. * Optional Retrofit Grill * Optional Color - Almond
Ratings: Heaters shall be available in wattages of 250 to 2,400, at 120, 208, 240, or 277 volts. Heaters shall provide air movement at 85 CFM.
Fan and Motor: Motor shall be shaded pole, permanently lubricated, C-frame type with impedance protection and sealed bearings. Motors shall be the same voltage as the heater. The motor and all wiring shall be totally isolated from the heating chamber for protection from heated air. The motor shall be equipped with a dynamically balanced four bladed aluminum impeller fan, located in the upper portion of the heatbox, and shall provide a down-flow heating pattern
Elements: Assemblies shall be constructed of coiled nickel chromium alloy, corrosion resistant wire strung thru a minimum of four rows of mica insulator. Element assemblies shall have factory provided connection to allow field modification to 50% wattage.
Thermal Overload: Heaters shall be equipped with thermal overload SMART LIMIT PROTECTION, which disconnects elements and motor in the event normal operating temperatures are exceeded. If thermal overload trips due to abnormal operating temperatures, thermal overload shall remain open until manually reset by turning the heater off for fifteen minutes. Automatic reset thermal overloads, which allow the element to continue to cycle under abnormal conditions will not be accepted.
Wall Can: The wall can shall be 22 gauge electro-galvanized steel and shall contain knockouts through which power leads are brought. The wall can shall be provided with a depth gauge, extending the full length of the wall can. The wall can shall be supplied with a factory installed grounding wire. Minimum Clearance to Floors and Sidewalls. Zero clearance to combustibles.
Grill: The grill shall be louvered, one piece design with rounded edges on all four sides, with rounded corners to prevent snags from contact with other materials. The grill shall be epoxy powder coated in the color specified on the by manufacture.
Approval: Heaters shall be listed and approved by Underwriters Laboratories.