Results You searched for: King Electric KT Series 120 Volt Kickspace Heaters Results Displayed: 1 - 17 of 17
This narrow profile heater is only 3½" tall and specifically designed to fit under kitchen or bathroom cabinets, providing warm comfortable air for a cold bathroom or kitchen floor saving valuable floor and wall space.
The squirrel cage blower in this heater has a smaller diameter than the wall heaters and therefore will make more sound than the PAW Series.
The optional KTG-24W Retrofit Grill allows for easy replacement of old style kick space heaters. Install heater and fit with long grill to cover existing cut-out. For application other than kick space, use KTG-OL Grill.
Check vinyl manufactures recommendation for surface temperature. Usually 750 Watts or lower is recommended for vinyl flooring under counters.
* Smart Limit Protection® * Dual Open Coil Element * C-Frame Motor * Squirrel Cage Blower * Low Profile * Dual Wattage * 20 Gauge Powder Coated Grill * Standard Color - Bright White * Safety limit turns off power to the element if it overheats and automatically resets. * 20 Gauge Electro-Galvanized Steel. * Approved for direct contact with building insulation. * Optional 1-Pole or 2-Pole unit mount thermostat 45°- 80°F operating range. * Optional Retrofit Grill * Optional Overlap Grill * Optional Colors - Almond or Black * Available in Stainless Steel
Ratings: Heaters shall be available in wattages of 500 to 1,500, at 120 volts or dual rated from 208 volts to 240 volts.
Blower and Motor: A tangential cylindrical blower, delivering 70 CFM, shall be driven by a shaded pole, permanently lubricated, C-frame type motor with impedance protection and sealed bearings. Motors shall be the same voltage as the heater.
Elements: Elements assemblies shall be dual element construction of coiled nickel chromium alloy, corrosion resistant wire strung through a minimum of four rows of mica insulator. Element assemblies shall have factory provided connection to allow field modification to 50% wattage.
Wall Can: The wall can shall be 22 gauge electro-galvanized steel and shall contain knockouts through which power leads are brought. The wall can shall be supplied with a factory installed grounding wire. Minimum Clearance to Floors and Sidewalls. Zero clearance to combustibles.
Grill: The grill shall be louvered, one piece design. The grill shall be epoxy powder coated in the color specified on the plans.
Approval: Heaters shall be listed and approved by Underwriters Laboratories.