Results You searched for: Cadet Register Plus Electric Fan Wall Heater. The premier choice for all rooms Results Displayed: 1 - 4 of 4
Cadet Register Plus Electric Fan Wall Heater. The premier choice for all rooms.
Cadet Register Plus In-wall Fan-forced Electric Wall Heater - Complete Unit Includes Wall Can and Heater Assembly and Grill - Thermostat required (not included.). The Register Plus is Cadet's premier fan forced heater line and is often chosen for its similar appearance to central system register vents. A large squirrel cage blower quietly provides increase airflow allowing for lower surface and air-at surface temperatures. An electronic wall mounted thermostat is recommended for optimum performance. Complete unit includes wall can, heater assembly, and grill.
The premier heater choice with similar appearance to a central system register vent.
Large squirrel cage blower provides increased airflow for lower surface temperatures and quiet performance.
Wall can designed for quick installation with mounting legs that minimize measuring time.
Manufacturer recommends cleaning every 6 months
Commercial grade steel element
High temperature manual reset: turns off heater if normal operating temperatures are exceeded
Warranty: 5 year warranty
Architectural Information: Fan forced electric air heaters shall be UL Listed, factory rated at 120V, 208V, or dual field rated 208V/240V. A 20 gauge wall mounting can with four knockouts shall be provided with each complete heater. The element and blower shall be of unitized construction and shall attach to wall can with a single screw. Elements shall be steel-finned type, with an oversized 25 amp rating at 240V high temperature manual reset limit switch. A tangential cylindrical blower delivering approximately 60 CFM (RM202), and 50 CFM (RM162 and RM151) shall be driven by an impedance protected motor with permanently lubricated, vibration isolated, dust sealed bearings. Metal grill shall be of one piece construction and finished with a powder coat paint system.
Technical Information: A thermostat is required. For optimum comfort use a Cadet electronic thermostat. Fan heaters and thermostats work best when installed on an inside wall. A double pole, built-in thermostat may be installed in the field. UL requires heater to be placed a minimum distance of 6” (15.2 cm) from adjacent surfaces and 4.5” (11.4 cm) from the floor. Manufacturer recommends installation of 12” from all surfaces. A 3’ (91.44cm) minimum clearance is required for furniture or other objects placed directly in front of heater.
NOTE: Manufacturer recommends installing heater assembly after walls are finished. Heater must be cleaned every six months minimum.