Home >> Unit Heaters (Blower) >> TPI Corp/Markel Taskmaster 5100 Series Horizontal or Vertical Mounted Fan Forced Unit Heater
Results You searched for: TPI Corp/Markel Taskmaster 5100 Series Horizontal or Vertical Mounted Fan Forced Unit Heater Results Displayed: 1 - 68 of 68
3.3 KW THROUGH 50 KW SUSPENDED FAN FORCED UNIT HEATERS AVAILABLE IN 1 OR 3 PHASE FOR ALL STANDARD VOLTAGES FROM 208V TO 480V THAT CAN BE MOUNTED TO PROVIDE HORIZONTAL OR VERTICAL DISCHARGE.
Heavy 18 Gauge welded steel cabinet with powder coated finishand control compartment housing a master terminal board with a hinged and latched access door, simplifying wiring, installation & maintenance.
Copper clad steel sheath element with continuously brazed steel finsformed to allow side draw through air flow.
All units come equipped with automatic reset type limit controls to de-energize the heater should an over-temperature situation occur.
FAN and MOTOR:
Totally enclosed, 1-speed, 1-phase, permanently lubricated, thermally protected motors with unit bearings on 3 KW - 20 KW models. Totally enclosed, 2-speed, 1-phase, permanently lubricated, thermally protected motors with sleeve bearings on 25 KW - 50 KW models. All motors mounted with rubber insulators to minimize vibration & noise. Fan over-ride purges unit of residual heat at shutdown.
Louvers are individually adjustable for directional control of air flowup to 15° from straight horizontal. Optional diffusers available for down flow (vertical dischage) applications.
Optional low voltage and line voltage thermostats available with an adjustable temperature range of 40°F to 90°F. Units with model numbers ending in CA1 are factory wired for low voltage controls. 25 KW through 50 KW units are designed for two stage heating operation.
Unit Heaters can be mounted for horizontal or vertical discharge.Applications up to 6000 Ft. See UH Series above 6000 Ft.ABS (American Bureau of Shipping) type approved.
FIELD INSTALLED OPTIONS:
• In-unit or wall mounted temperature control thermostats low or line voltage.