Results You searched for: PZ Series 240 Volt Wall Heaters Results Displayed: 1 - 17 of 17
Used in apartment applications where a high quality dependable heater is desired and the wattage is specified on the plans. This heater has all the qualities of the famous Pic-A-Watt®, but without the features of picking the wattage at the time of installation.
* Steel Fin Element * C-Frame Motor * Squirrel Cage Blower * 20 Gauge Powder Coated Grill with contemporary die formed round corners. * Standard Color - Bright White * Bi-Metallic Limit on Manual Reset Limit * Optional 1-Pole or 2-Pole unit mount thermostat 45°- 80° * Optional Surface Wall Box * Optional Color - Almond
Ratings: Heaters shall be available in wattages of 250 to 2,000, at 120, 208, 240, or 277 volts.
Blower and Motor: A tangential cylindrical blower, delivering 65 CFM, shall be driven by a shaded pole, permanently lubricated, C-frame type motor with impedance protection and sealed bearings. Motors shall be the same voltage as the heater.
Elements: Elements assemblies shall be non-glowing design. Element assemblies shall consisting of steel sheathed heating tubes in a furnace brazed, plate finned, block design. Each sheathed tube shall contain a coiled Ni-Chrome wire, embedded in an insulator of magnesium oxide. The element assembly shall provide the specific wattage indicated on the plans.
Thermal Overload: Heaters shall be equipped with thermal overload protection, which disconnects elements in the event normal operating temperatures are exceeded. The thermal overload protection device shall automatically reset when normal operating temperatures are reached or manual reset by turning the thermostat down for 15 minutes.
Wall Can: The wall can shall be 20 gauge electro-galvanized steel and shall contain a minimum of three (3) knockouts through which power leads are brought. The wall can shall have a depth gauge indicator, and a factory installed, insulated and stranded copper grounding wire. Minimum Clearance to Floors and Sidewalls. Zero clearance to combustibles.
Grill: The grill shall be louvered, one piece design with rounded edges on all four sides, with rounded corners to prevent snags from contact with other materials. The grill shall be epoxy powder coated in the color specified on the plans.
Approval: Heaters shall be listed and approved by Underwriters Laboratories or similar agencies.